<!DOCTYPE html>
<html lang="mr">
<head>
    <meta charset="UTF-8">
    <title>नागरिक प्रमाणपत्र</title>
    <style>
        body {
            font-family: 'Mangal', Devanagari, serif;
            padding: 40px;
        }
        .header, .footer {
            text-align: center;
        }
        .content {
            margin-top: 30px;
        }
        /* .sub-header {
            text-align: right;
        } */
        .line {
            border-bottom: 1px solid #000;
            display: inline-block;
            min-width: 100px;
        }
        .points {
            margin-top: 20px;
        }
        .points li {
            margin-bottom: 10px;
            margin-left:5%;
        }
        p{
            font-size:18px;
        }
         table, th, td {
      border: 1px solid black;
      border-collapse: collapse;
    }
    th, td {
      padding: 8px 12px;
      text-align: center;
    }
    table {
      width: 100%;
      margin-bottom: 20px;
    }
    h2 {
      text-align: center;
      text-decoration: underline;
    }
    .section-title {
      font-weight: bold;
      margin-top: 30px;3
      margin-bottom: 10px;
    }
    .note {
      font-style: italic;
      margin-top: 5px;
    }
    </style>
</head>
<body>

    <div class="header">
        @php
        $logoData = file_get_contents(public_path('admin/images/favicon.png'));
        $logoData1 = file_get_contents(public_path('admin/images/RajyabhishekLogo.jpeg'));
        $logoData2 = file_get_contents(public_path('admin/images/13.jpeg'));
        $base64Logo = base64_encode($logoData);
        $base64Logo2 = base64_encode($logoData2);
        $base641Logo = base64_encode($logoData1);
        @endphp
       <img src="data:image/png;base64,{{ $base64Logo }}" alt="Logo" height="75" width="75">
       <img src="data:image/png;base64,{{ $base641Logo }}" alt="Logo" style="float:left; margin-top:35px;" height="150" width="150">
       <img src="data:image/png;base64,{{ $base64Logo2 }}" alt="Logo"  style="float:right;margin-top:35px;" height="150" width="150">
       <div class="rox">
        <h2>मिरा भाईंदर महानगरपालिका</h2>
        <p>स्व.इंदिरा गांधी भवन,मुख्य कार्यालय, छत्रपती शिवाजी महाराज मार्ग, भाईंदर (प.),ता.ठाणे-४०११०१</p>
        <p>दूरध्वनी क्र.२८१९२४८</p>
        <h3>अग्निशमन ना-हरकत दाखला देणे</h3>
       </div>
    </div>
<hr>
<hr style="1px solid #000; height:5px; background-color:#000;">
     <div class="sub-header">
        <div class="row d-flex">
        <p>जा.क्र. मनपा/सां/ {{ str_pad($data->id, 4, '0', STR_PAD_LEFT) }}/ 2025-2026
&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;
&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;
&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;
        दि. <span class="line">{{ \Carbon\Carbon::parse($data->created_at)->format('d') }}</span> / <span class="line">{{ \Carbon\Carbon::parse($data->created_at)->format('Y') }}</span></p>
        </div>
    </div>

    <p>To,<br>
         The Assistant Director Town Planning,<br>
        Mira Bhaindar Municipal Corporation,<br>
        Dist :- Thane,
    </p>

    <p style="margin-left:20%;"><strong>Sub :</strong> N. O. C. stipulating fire protection and fire fighting requirements for the high rise ---------------<br>
        Building Wing/No./Type------------ of M/s. ---------------------.” on plot bearing Old S. No./ H. No.<br>
        ------------- New S. No./H. No. --------------- at village ------------------, Tal & Dist. Thane</p><br>

    <p style="margin-left:20%;"><strong>Ref :<br></strong>1) An Application received From M/s. ----------------------- Architects, Dated ---------------.<br>
                                                            2) Built up area certificate received From M/s. -------------------- Architects, Dated ---------------.<br>
                                                            3) Appointment letter from M/s. --------------------------------. Dated -----------------.<br>
                                                            4) ID card of Council of Architectural Registration.<br>
                                                            5) Status report of M/s. ------------------ Architects, Dated ----------------------.</p>
                                                            <br>


    <div class="content">
        <p>With reference to the above M/s. ---------------------, architect on behalf of M/s. -------------------------------.
            had submitted an application for grant of “Provisional No-Objection Certificate” from this office for proposed
            construction of High rise ------------------- Building Wing/No./Type G + -------- Floors, at the above mentioned
            S. No. The Plot area of is ------------------- Sq. Mtrs. The site accessible from ----------------- mtr. D. P. road. The
            height of the building is proposed ----------------- meter. </p><br>

            <p>This is a proposal for the construction of high-rise ------------------ building Wing/No./Type . At present plot
is vacant. </p><br>
           <p>The proposed building is propose to use Ground floor for ------------- + ------- floors are proposed to use for
------ purpose.</p><br>

           </h3><strong>OBSERVATIONS<strong></h3><br>
             <h5><strong> a) STAIRCASES</strong></h5><br>
             <p>The Proposed building is provided with Two Enclosed type staircases with the width of ---- mtr. & ---- mtr.
each. The Staircases are leading from Ground to terrace floor</p><br>
&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;The area wise (Gross) details of said buildings are as under:<br>

   <table>
    <thead>
      <tr>
        <th>FLOORS</th>
        <th>Area in Sq. Mtr. Wing-A</th>
      </tr>
    </thead>
    <tbody>
      <tr>
        <td></td>
        <td></td>
      </tr>
      <tr>
        <td><strong>TOTAL</strong></td>
        <td></td>
      </tr>
    </tbody>
  </table>

  <div class="section-title">THE FLOOR-WISE USER OF THE BUILDINGS ARE AS UNDER.</div>

  <table>
    <thead>
      <tr>
        <th>Floor</th>
        <th>Occupancy Wing-A</th>
      </tr>
    </thead>
    <tbody>
      <tr>
        <td>----</td>
        <td>----</td>
      </tr>
    </tbody>
  </table>

  <div class="section-title">REFUGE AREA: Building Wing-A (Ground level 0.00mts)</div>

  <table>
    <thead>
      <tr>
        <th>Refuge Floor</th>
        <th>Required Refuge area in sq. mtrs.</th>
        <th>Permissible Refuge area in sq. mtrs.</th>
        <th colspan="2">At the height of refuge floor from ground level in mtrs.</th>
      </tr>
      <tr>
        <th colspan="3"></th>
        <th>Proposed</th>
        <th>Height</th>
      </tr>
    </thead>
    <tbody>
      <tr>
        <td>----</td>
        <td>----</td>
        <td>----</td>
        <td>----</td>
        <td>---- mtr</td>
      </tr>
    </tbody>
  </table>

  <p>Terrace Floor<br>
  In addition to that terrace of the building will be treated as refuge area. Excess refuge area shall be counted towards FSI</p>
  <p>The Site is accessible from 18.00 mtr wide DP road.</p>

  <div class="section-title">THE DETAILS OF STAIRCASES & LIFTS</div>

  <table>
    <thead>
      <tr>
        <th>Staircase Description</th>
        <th>Width of Staircase</th>
        <th>No. of Staircases</th>
      </tr>
    </thead>
    <tbody>
      <tr>
        <td>Building Wing- ------- <br> Common for the buildings Leading from Ground to terrace</td>
        <td>--- mtr.<br> --- mtr.</td>
        <td>--- Nos.<br> --- Nos.</td>
      </tr>
    </tbody>
  </table>

  <p class="note">The proposed staircases are enclosed type and are internally located and adequately ventilated to outside air. <br>
  <strong>The staircases meet the following requirements.</strong></p>
  <br>
  <table>
  <thead>
    <tr>
      <th>Lift Types</th>
      <th>Profile</th>
      <th>Nos. of lifts</th>
    </tr>
  </thead>
  <tbody>
    <tr>
      <td colspan="3"><strong>Building Wing- -------</strong></td>
    </tr>
    <tr>
      <td>Lifts</td>
      <td>Leading from Ground to Top floor</td>
      <td>--- Nos.</td>
    </tr>
    <tr>
      <td>Fire Lift</td>
      <td>Leading from Ground to Top floor</td>
      <td>--- Nos.</td>
    </tr>
  </tbody>
</table>
<br>
<p>One lift per wing shall be converted into fire lift as per norms. </p><br>
<p>The lift lobby & common corridor at each floor level is directly ventilated to outside air as shown on the plan</p><br>

<p>
    The Asst. Director, Town Planning, Mira Bhainder Municipal Corporation is requested to scrutinized the
plans as per amended UDCPR & verify civil work and all other requirements pertaining to Civil Engineering side
including open spaces, corridors, staircases, amendments, height, refuge area in sq. mtrs. & floor occupancy of the
building. If any changes in the plans other than mentioned above then the proposal shall be referred back to this
department for revised NOC till then further process shall not be permitted
</p>
<br>

<p>During construction stage and before the final occupation architect/developer has agreed to comply
additional requirement stipulated by Fire Brigade Department as may be feasible.</p>
<br>

<p>In view of above, as per as this department is concerned there is no objection for the construction of a highrise residential buildings is propose to use Ground floor for ------------- + ------- floors are proposed to use for ------
purpose with the total average height of ---- mtr from general ground level up to terrace level. signed in taken of
approval, subject to satisfactory compliance of the following requirements;
</p><br>
<h3><strong>1.) ACCESS: </strong></h3><br>
i) There shall be no compound wall on road side of the building.<br>
ii) All access & fire tender access should be free of encumbrances. Entrance gate if provided shall be of not less
than 6.00 meters width each shall be provided, at locations marked on the plan. Archways, if any over the
entrance gates, shall have height clearance of not less than 5.00 mtrs<br>

<h3><strong>2.) PROTECTION TO STRUCTURAL STEEL:</strong></h3><br>
i) All the structural steel members i.e. columns, beams etc., shall be protected with the 02 hours fire resisting
materials and methods as stipulated under IS 1942 1960 as application for residential building.<br>
ii) certificate to that effect that the fire resistance protection has been provided as above shall be furnished from the
Structural Engineer as the time of application for occupying the building.
<br>

<h3><strong>3.) COURTYARDS :</strong></h3><br>
i) The available courtyards/ open space on all the sides of the building shall be paved, suitably to bear the load
of fire engines with point load of 10 kgs./cm2. And the porch if any, shall have clear height of not less than
5.00 mtrs.<br>
ii) All the courtyards shall be in one plane and mandatory open space shall be clear of any obstructions including
tree.<br>
iii) The courtyards shall be kept free from obstruction at all times.<br>

<h3><strong>4.) STAIRCASE: </strong></h3><br>
i. The flight width of staircases shall be maintained as shown in the enclosed plans.<bR>
ii. The layout of staircases shall be enclosed type as shown in the plan throughout its height and shall be
approached (gained) at each floor level at least two hours fire resistant self closing door placed in the enclosed
wall of the staircase.<br>
iii. Externally located staircases and lobbies adequately ventilated to outside air.<br>
iv. Permanent vent at the top equal to 5% of the cross sectional area of the staircase shall be provided.<br>
v. Openable sashes or R.C.C. grills with clear opening of not less than 0.5 sq. mtrs. per landing on the external
wall of the staircase shall be provided.<br>
vi. No combustible material shall be kept or stored in staircase / passage and shall be kept unobstructed all time.<br>
vii. Internal staircases for the duplex/triplex shall be provided FRD on lower floor level.<br>

<h3><strong>5.) STAIRCASE AND CORRIDOR LIGHTINGS:: </strong></h3><br>
i. The staircase and corridor lighting shall be on separate circuits and shall be independently connected so that
they could be operated by one switch installation on the ground floor control room easily accessible to fire
fighting staff at any time irrespective of the position of the individual control of if any.<br>
ii. Staircase and corridor lighting shall also be connected to alternate supply and DG power supply<br>
iii. Double throw switches should be installed to ensure that lighting in the staircase and the corridor do not get
connected to two sources of supply simultaneously. A double throw switch shall be installed in the service
room to terminate the stand by-supply.<br>
iv. Emergency lights shall be provided in the staircases/corridors.<br>

<h3><strong>6.) FIRE TOWER/ FIRE ESCAPE STAIRCASES: </strong></h3><br>
i) The smoke check lobby with evacuation lift/Fireman lift shall have positive level difference of minimum 75
mm. with respect to staircase landing or mid-landing level to avoid ingress of water in fireman lift shaft.<br>
ii) For enclosed firefighting shaft, the shaft’s lobby should have floor plan duly displayed for the information
of fire fighters.<br>
iii) The lobby of Fire Tower or Fire Escape Staircase shall be a pressurized or smoke check lobby.<br>
vi). Pressurization system shall be interconnected with manual or automatic alarm system . <br>

<h3><strong>7.) CORRIDOR / LIFT LOBBY: </strong></h3><br>
ix). Corridor / lift lobby at each floor level shall be naturally ventilated as shown in plan.<br>
x). The common corridor / lift lobby at each floor level shall be kept free from obstructions at all times.<br>
xi). Self glowing / fluorescent exit signs in green color shall be provided showing the means of escape for
entire building.<br>
xii). Portable lights/insta lights shall be provided at strategic locations in the staircase and lift lobby<br>


<h3><strong>PRESSURIZED CORRIDOR I LIFT LOBBY : </strong></h3><br>
The lift lobbies/ common corridor at Basement and Ground floor level shall be pressurized in the event of fire. the
pressure in the enclosed lift lobbies shall be maintained not less than 2.5 mm W.G.<br>

<h3><strong>PRESSURIZATION</strong></h3><br>
a. The proposed smoke management system for the building shall be a zoned control system utilizing clustered
Air Handling Units (AHU's) located al such floor. The system shall include separate fans and AHU's that will
provide stairwell and elevator pressurization, as well as lift lobby pressurization. When smoke or a fire is
detected by the fire alarm system as per the NBC codes a minimum positive pressure between 25 and 30 Pa
shall be maintained in the lobby and a positive pressure of 50 pa shall be maintained in the lift shaft as well as
internal staircases.<br>
b. Smoke / Fire dampers shall be provided in accordance with NFPA within supply air ducts and return air ducts
at AHU room wall crossings wherever provided, at fire rated wall crossings, and at walls between adjoining
fire zones. Smoke detectors shall be provided in return air duct to the AHU's and shall shut down the ARU's
serving the floor space upon smoke detection,<br>
c. Pressurization system shall be interconnected with manual or automatic alarm system.<br>

<h3><strong>8). ELECTRIC CABLE SHAFTS, SERVICES & METER ROOM </strong></h3><br>
i. Electric cable shafts shall be exclusively used for electric cables and should not open in staircase enclosure.<br>
ii. Inspection doors for shafts at the each floor level shall have two hours fire resistance.<br>
iii. Electric shafts shall be sealed at each floor level with non combustible materials such as vermiculite concrete.
No storage of any kind shall be done in electric shaft.<br>
iv. Electric wiring/ cable shall be non-toxic, non-flammable, low smoke hazard having copper core / fire resistance
for the entire building with provision of FF AB/MCB.<br>
v. Electric meter room shall be provided at the location shown in the plan. It shall be adequately ventilated & easily
accessible.<br>
vi. Low and medium voltage wiring running in shaft and in false ceiling should run in separate conduits;<br>
vii. Water mains, telephone lines, intercom lines, gas pipes or any other service line should not be laid in the duct for
electrical cables, use of bus bar/solid rising mains instead of cables is preferred.<br>
viii. Preferably bus bar system shall be installed from ground to all upper floors main supply.<br>
ix. Separate circuits for fire fighting pumps, lifts, staircases and corridor lighting and blowers for pressurizing system
shall be provided directly from the main switch gear panel and these circuits shall be laid in separate conduit
pipes, so that fuse in one circuit will not affect the others. Such circuits shall be protected at origin by an automatic
circuit breaker with its no-volt coil removed.<br>
x. Automatic smoke detector system shall be provided in each electric shaft on each floor along with response
indicator which shall be connected to main control panel board on ground floor level and each floor level.<br>
xi. Master switches controlling essential service circuits shall be clearly labeled and shall be placed at control room
on ground floor.<br>

<h3><strong>9.) FALSE CEILING (if provided):</strong></h3><br>
False ceiling if provided in the building shall be of non combustible material. Similarly, the suspenders of the false
ceiling shall be of no combustible materials.<br>

<h3><strong>10) MATERIALS FOR INTERIOR DECORATION/FURNISHING</strong></h3><br>
The use of materials which are combustible in nature and may spread toxic fume/gases should not be used for interior
decoration/furnishing, etc <br>

<h3><strong>11)LIFTS</strong></h3><br>
<h4><strong>A. PASSENGER LIFT</strong></h4><br>
i. Walls enclosing lift shall have a fire resistance of not less than two hour.<br>
ii. Shafts shall have permanent vent of not less than 0.2 sq mtrs in clear area immediately under the machine
room.<br>
iii. Landing doors and lift car doors of the lifts shall be of steel shuttered with fire resistance of one hour. No
collapsible shutter shall be permitted<br>
iv. Fire lift shown in the plan shall be as per specifications laid down under the regulations, a toggle switch
shall be provided to this lift for the use of Firemen<br>
v. Threshold of non combustible material shall be provided at the entrance of each landing door.<br>
vi. All lifts well shall be pressurized including fire lift.<br>

<h4><strong>B. FIRE LIFT:</strong></h4>
i. Walls enclosing lift shafts shall have two hours fire resistance.<br>
ii. The shafts shall have permanent vent equal 0.2 sq.mtr, clear area under the Lift Machine room.<br>
iii. Landing doors and lift car doors shall be of steel shuttered type with one hour fire resistance. No collapsible
shutters shall be provided.<br>
iv. To enable fire services personnel to reach the upper floor with the minimum delay, one fire lift shall be provided
and shall be available for the exclusive use of the firemen in an emergency and the directly accessible to every
dwelling or each floor.<br>
v. The lift shall have a floor area of not less than 1.4 sq mtrs, with a minimum dimension of 1.12 mtrs. It shall
have loading capacity of not less than 545 kg (8persons lift) with automatic closing doors.<br>
vi. There shall be an alternate electric supply of an adequate capacity apart from the normal electric supply the
building and the cables run in a route safe from fire, i.e. within the lift shaft. In case of failure normal electric
supply, it shall automatically trip over to alternate supply.<br>
vii. The operation of fire lift should be by a simple toggle or two button switch situated in glass-fronted box
adjacent to the lift at the entrance level. When the switch is on, landing call points will become inoperative
and the list will be on car control only or on priority control device. When the switch is off, the lift will
return to normal working. This lift can be used by the occupants in normal times.<br>
viii. The words 'Fire lift' shall be conspicuously displayed in florescent paint on the lift landing door at each floor
level & There should of non combustible material shall be provided at the entrance of each landing door.<br>
ix. Except Service Lifts, other lifts shall be converted into Fire Lifts conforming to relevant regulations. <br>


<h4><strong>12). CAR PARKING:<br>
A. HORIZONTAL CAR PARKING</strong></h4>
i. Car parking shall be permitted in the designated area.<br>
ii. Drainage of the car parking area of all the levels shall be laid independent from that of the buildings & it shall
be provided with catch pit & fire trapped before connecting the building drainage or Municipal drainage.<br>
iii. Drainage of the car parking areas at all the levels shall be so laid as to prevent any overflow in the staircase,
lift shaft etc.<br>
iv. The parking area shall not be used for dwelling purpose & repairing !maintenance purpose, at any time.
Dwelling use of naked light/flame, repairing /maintenance of vehicles shall be strictly prohibited in the
parking area.<br>
v. Repairing / servicing of cars, use of naked light shall not be permitted in the car parking areas.<br>
vi. The drive way shall be properly marked & maintained unobstructed. <br>
vii. The Automatic Sprinkler System provided to the entire car parking area . <br>


<h4><strong>B. STACKED CAR PARKING:</strong></h4><br>
i. Structural design: The SA-FAMCP shall be constructed of structural steel construction.<br>
ii. Vertical deck separation For SA-FAMCP having multi-car parking level, vertical separation between the
upper & lower decks by using the non perforated and non combustible materials. (structural steel plate) shall
be provided. This is to minimize direct impingement of flame to the car in the upper deck and also to prevent
dripping of any possible leaking fuel to the lower deck.<br>
iii. Elements of the staked car parking structure shall have 1 hr. fire resistance, Each car parking deck shall have
1 hr. fire resistance.<br>
iv. Parking area shall be accessible by trained staff when carrying out the maintenance work.<br>
v. The parking system is to be ceased during the maintenance operation.<br>
vi. Automatic sprinkler system shall be provided so as to cover each car with a sprinkler head as per relevant IS
specification.<br>
vii. If depth of the pit is more than 06 mtrs. And if height of the parking is more than 12 mtrs then separate
staircase having flight width minimum of 0.90 mtrs shall be provided for.<br>
13. Fire Fighting Shaft (Fire Tower) with Fireman Lift (on Landing and Mid landing level) as approved in plans
shall be complied with NBC 2016,Part IV, 2.24.<br>

<h4><strong>14.) SMOKE MANAGEMENT SYSTEM:</h4></strong><br>
a. Escape routes like staircase, common corridor, lift lobbies, etc. shall not be used as return air passages.<br>
b. Direct expansion system shall not be used.<br>
c. The ducting shall be constructed of substantial gauge/metal in accordance with IS: 655:1963 metal air duct
(revised).<br>
d. Wherever the ducts pass through fire walls or floors, the opening around the ducts shall be sealed with fire
resisting material such as vermiculite concrete or glass wool. A. C. ducting shall not pass through staircase
well.<br>
e. As far as possible metallic ducts shall be used even for return air instead of space above false ceiling.<br>
f. The material used for insulating the ducts (inside or outside) shall be of non combustible type such as glass
wool or spun glass with neoprene facing etc.<br>

<h4><strong>15.) FIRE FIGHTING REQUIREMENTS shall be provided as follows:</strong></h4>
<div class="section-title">FIRE-FIGHTING INSTALLATION DETAILS</div>

<table>
  <thead>
    <tr>
      <th>Fire-Fighting Installation</th>
      <th>Provision</th>
    </tr>
  </thead>
  <tbody>
    <tr>
      <td>Underground water storage Tank</td>
      <td>As per NBC 2016</td>
    </tr>
    <tr>
      <td>Overhead Water storage Tank</td>
      <td>As per NBC 2016</td>
    </tr>
    <tr>
      <td>Wet Riser Cum Down Comer</td>
      <td>As per NBC 2016</td>
    </tr>
    <tr>
      <td>Automatic Sprinkler system</td>
      <td>IS:15105</td>
    </tr>
    <tr>
      <td>Automatic detection & Fire Alarm system</td>
      <td>IS:11360-1985, IS: 2189:2008</td>
    </tr>
    <tr>
      <td>Fire Pump</td>
      <td>As per NBC 2016, IS: 15301:2003</td>
    </tr>
    <tr>
      <td>Signages</td>
      <td>
        IS:9457 for Safety<br>
        IS:12349 for Fire Protection Safety Signs<br>
        IS:12407 for Graphics symbols for Fire Protection Plan.
      </td>
    </tr>
    <tr>
      <td>Fire Extinguishers</td>
      <td>IS:2190 and 15683</td>
    </tr>
    <tr>
      <td>Courtyard Hydrants</td>
      <td>IS:3844 -1989</td>
    </tr>
    <tr>
      <td>Alternate source of supply</td>
      <td>As per DCR</td>
    </tr>
    <tr>
      <td>Manual call points</td>
      <td>As per NBC 2016, IS: 2189:2008</td>
    </tr>
    <tr>
      <td>Public Address system</td>
      <td>As per NBC 2016, IS: 1881:1998</td>
    </tr>
    <tr>
      <td>Fire Brigade Inlet Connection</td>
      <td>IS:14933 -2001</td>
    </tr>
    <tr>
      <td>Fire Drill</td>
      <td>As per NBC 2016</td>
    </tr>
  </tbody>
</table>
<br>

<h4><strong>16) FIRE FIGHTING REQUIREMENTS :</strong></h4>
<h3><strong>A) OBSERVATIONS OF OVER HEAD WATER TANK (According to Plan)(FOR EACH BUILDING)</strong></h3>
   Overhead tank for each wing with 10,000 liter capacity is shown in the plan.<br>

<h4><strong>SUGGESTIONS FOR OVERHEAD TANK </strong></h4>
The stability of the Terrace should be maintained to bear the load of the water tank.<br>
 A separate partition wall shall be provided between the Domestic & Fire Tank.<br>
Fire tank shall be connected with Booster Pump on Terrace.<br>
The tank shall be connected to the wet riser through a booster pump through a non return valve and gate
valve.<br>

<h4><strong>B) OBSERVATIONS OF UNDERGROUND WATER STORAGE TANKS (According to Plan)</strong></h4><br>
Common Under Ground Water tank for fire fighting purpose for all buildings with 600000 liter capacity is
shown in the plan.<br>

<h4><strong>SUGGESTIONS FOR UNDERGROUND WATER STORAGE TANKS:</strong></h4>
<strong>Water supply required shall entirely accessible to the fire engines of the local fire service.
Provision of suitable number of manholes shall be made available for inspection, repairs, & insertion of
suction hoses etc.<br>
The covering slab shall be able to bear the load of fire engines weighing up to 48 M.T. each with a point<br>
load of 10 kgs/sq. cm. at any given point when the slab forms a part of pathway/driveway.<br>
Applicant shall be provide a partition wall between domestic & fire tank.<br>
The layout of tank shall be got approved from MBMC department prior to erection.<br>
The tanks shall be connected to sprinkler system.<br>
All the water tanks shall be interconnected by piping network for maximum and continuous supply of
water to the Fire fighting system.<br>
</strong>
<br>
<h4><strong>C) WET RISER: (For Each Building)</strong></h4><br>
Wet Riser of Internal Diameter of 150 mm of G.I.”C” Class Pipe shall be provided in the duct adjoining the
staircase with hydrant outlet & Hose Reel on each floor. In such a way as not to reduced the width of the
staircase/common corridor. Pressure reducing discs for orifices shall be provided at lower level. So as not to exceed
on the pressure of 5.5 Kgs. / Sq. cm. A Fire Service inlet on the static tank directly fronting Courtyards shall
be provided to connect the mobile pump of fire service to the Wet Riser. The Wet Riser should be
pressurized type & automatic in operation, with jockey Pump of suitable capacity. The wet risers shall be extended
from ground floor up to terrace level. Wet riser outlet and hose reel at a distance of 100 feet. shall be provided on
periphery of all podium / parking floors.<br>

<h4><strong>D) FIRE SERVICE INLET :</strong></h4><br>
i) Fire service inlet shall be provided to refilled U.G. tank as well as to feed riser system by passing the fire pump &
to feed sprinkler system.<br>
ii) Operating switches of fire pumps shall be also provided in glass fronted boxes at ground floor . <br>


<h4><strong>E) PUBLIC ADDRESS SYSTEM:</strong></h4><br>
The entire building shall be provided with the public address system in common areas with main control panel at
ground floor reception area and in BMS Room.<br>

<h4><strong>F) AUTOMATIC SMOKE DETECTION SYSTEM :</strong></h4><br>
Automatic smoke detection system shall be provided in commercial, electric meter room & lift machine room,
Control / BMS Room and in electric shaft at every floor level with response indicator; same should be connected to
main control panel on ground floor level in BMS Room, as per IS specification. <br>

<h4><strong>G) FIRE PUMP, BOOSTER PUMP AND JOCKEY PUMP:</strong></h4><br>
i. Wet-riser shall be connected to a fire pump ( two electrically operated and one DG operated) at ground level of
capacity of not less than 2850 liters/min. capable of giving a pressure of not less than 3.2 kgs/ sq. cms. at the
top most hydrant.<br>
ii. Booster pump of 900 liters/min. capacity giving a pressure of not less than 3.2kgs./sq. cms. at the top most
hydrant Out let of the wet-riser shall be provided at the terrace level.<br>
iii. Electric supply (normal) to these pumps shall be independent circuit.<br>
iv. Separate jockey pump shall be provided to Wet riser system to keep system pressurized.<br>
v. Operating switches for booster pumps shall be also provided in glass fronted BASIN boxes in lift lobbies on
each floor at prominent place. <br>
vi. Operating switches of fire pumps shall be also provided in glass fronted boxes at ground floor.<br>
vii. All above pumps should be surface mounted or vertical turbine type cm (submersible pump not permitted) pump
along with adequate size of pump room <br>

<h4><strong>H) STAND BY PUMP:</strong></h4><br>
<strong>i) Provide required number of sets of pumps each consisting of two electric and one diesel pump (stand by)
of capacity 2280 litre/min and two electric pump of capacity 180 litre/min </strong><br>

<h4><strong>I) EXTERNAL HYDRANTS.</strong></h4><br>
Courtyard hydrants shall be provided at distance of 30.00 mtrs each within the confines of the site of the wet risercum-down comer. Hose box with two non percolating ISI marked hoses (length not less than 15 mtrs.) & branch
shall be equally distributed on ground floor, podium floor, as well as on each floor near the hydrant outlet.<br>

<h4><strong>J) EMERGENCY POWER FOR FIRE & LIFE SAFETY SYSTEM</strong></h4><br>
Emergency power for Fire & Life Safety System shall comply with NBC 2016, Part IV.3.4.6.2.<br>

<h4><strong>a) ALTERNATE SOURCE OF POWER SUPPLY.</strong></h4><br>
An alternate source of LV/HV supply from a separate substation as well as from a diesel generator with
Auto/Manual changeover over switch shall be provided for fire pumps, booster pump, sprinkler pump, jockey
pump, staircase and corridor lighting circuits and fire alarm system, detection system, public address system,
voice evacuation system etc. It shall be housed in separate cabin.<br>

<h4><strong>b) DEISEL GENERATOR SET</strong></h4><br>
a. Entire Installation of D.G. Set shall be conforming to the Indian Electrical Act/ Rules in practice.
b. A deep tray shall be kept under the fuel tank of the D.G. Set to collect the spillage and the same shall be
disposed off daily without fail.
c. Electric wiring shall be having copper core having the fire resistance and low smoke hazard cables for the
entire building with provision of ELCB/MCB.
d. The capacity of the D.G. Set shall be as per Indian Electrical Act / Rules in practice.
e. Adequate ventilation for Switchgear Room is essential to prevent condensation.
f. The D. G. set shall be properly grounded.
g. Exhaust of the D.G. set shall not be directed into the exit/entrance or any adjoining structures.
h. Sand bed of at least 6inch thickness shall be provided below the D. G sets
i. Electric cable of the D.G set shall be of FRLS type.
j. Proper ventilation shall be provided to the D. G set.
k. Not more than 30litres of spare diesel shall be stored in its original corner near the D.G set away from electric
switches or source of ignition.
l. Electric cable laid in the cable trench shall be coated with fire reliant material.
m. Automatic built-in circuit breaker shall be provided to the D. G sel.
n. Rubber pad shall be provided to the D.G. Set for absorb vibration, if any.
o. The D.G. Set area shall be kept prohibited and no unauthorized personsshall be allowed to enter in the area.
p. Two Dry Chemical Powder (ABC) type fire extinguishers of 9 kgs. Capacity each with ISI certification mark
coupled with four buckets filled with dry, clean sand shall be kept in the D.G. Set area.
<br>


<h4><strong>K) PORTABLE FIRE EXTINGUISHERS:</strong></h4>
i. One dry chemical powder type fire extinguisher of 09 kgs. capacity having1.S.I. certification mark and two
sand buckets filled with dry cleaned sand shall be kept in electric meter room as well as in lift machine
room.<br>
ii. One dry chemical powder type fire extinguisher of 09 kgs capacity having 1.S.). certification mark and two
sand buckets filled with dry cleaned sand shall be kept at ground & each level of podium for every 100 sq mtr
area.<br>
iii. One dry chemical powder type fire extinguisher of 06 kgs. capacity having 1.S.I. certification mark shall be
kept on each floor level at prominent place & refuge area.<br>
iv. All above fire extinguishers should be placed on each floor level as per IS:2190 of 1992.<br>

<h4><strong>L) FIRE ALARAM SYSTEM / FIRE DETECTION SYSTEM:</strong></h4>
a. The building shall be provided with intelligent analog addressable fire alarm system with microprocessor based
main control panel at ground floor level and addressable call points and hooters at each floor level. The design
of fire alarm system shall be in accordance with I.S. specification and based on NFPA 72 guidelines (as per
2010 edition).<br>
b. The addressable fire alarm system shall be equipped with the latest evacuation features such as digital voice
evacuation capabilities; fire fighters telephone system, directional sounders etc. The main entry / exit points
shall be provided with fire fighters interactive interface to enable viewing of critical information in event of
fire.<br>
c. Access control system, close circuit cameras shall be installed in the entire building & connected at the control
room.<br>


<h4><strong>M) FIRE DRILLS / EVACUATION DRILLS:</strong></h4>
Fire Drills and evacuation drills shall be conducted regularly in accordance with fire safety plan of building at least
once in a three month in consultation with Mumbai Fire Brigade and log of the same shall be maintained.<br>

<h4><strong>N) PUBLIC ADDRESS SYSTEM:</strong></h4>
The entire building shall be provided with the public address system in common areas with main control panel at
ground floor reception area and in BMS Room.<br>

<h4><strong>O) VOICE EVACUATION SYSTEM:</strong></h4><br>
The manual voice evacuation system input to be provided at the control room & shall be integrated to Fire Alarm
system so as to facilitate the co-ordination activities in case of fire emergencies. The actuation of the fire alarm
control panel shall automatically activate the Voice Evacuation system. A pre-recorded message shall be broadcast
on the affected floor, one floor below & two floors above the affected floor.<br>

<h4><strong>17. SERVICE DUCT:</strong></h4><br>
All service ducts shall have 2 hr. fire resistance. Inspection door of the service ducts shall have 2 hr. fire resistance.
Duct for water service, drainage line, shall be separate from that of electrical cable duct.<br>

<h4><strong>18. TRAINED FIRE OFFICER FIREMEN AND SECURITY GUARDS:</strong></h4>
a. A qualified fire officer with qualification of min. Sub Officer Course and Firemen with qualification
of Firemen Course from Directorate Maharashtra Fire Services shall be appointed for round the clock
duty.<br>
b. The trained security having basic knowledge of fire fighting & fix met installation shall be provided
/ posted in the building round the clock.<br>
c. Maintenance of all the first aid fire fighting equipments, fixed installation other fire fighting
equipments / appliance in good working condition at all times.<br>
d. Imparting training to the occupants of the building in the use of firefighting equipment provided on
the premises & kept them informed about the med other emergency evacuation procedures.<br>
e. To liaise with the City Fire Brigade on regular & continual basis.<br>

<h4><strong>19. DISASTER MANAGEMENT PLAN:<strong></h4>
a) Disaster management plan for fire & other emergency shall be prepare and kept ready at the control
room.<br>
b) The mock drill with the designated fire marshal for any operation of disaster management plan shall
be
 carried out regularly after occupation as per National building code.<br>
c) Emergency exit route plan framed in glass shall be displayed in the common corridor, cross passages,
staircase lift lobbies of each floor level.<br>

<h4><strong>20. FIRE CONTROL ROOM : (BMS ROOM)</strong></h4><br>
a) Separate Fire Control room shall be provide with well qualified man power shall be established
on ground floor.<br>
b) The Fire Control Room (FCC) shall comply with NBC 2016, Part IV.3.4.12.<br>
c) Plan of each floors indicating means of egress as well escape shall be maintained.<br>

<h4><strong>21. ELECTRIC SUB-STATION (DRY TYPE):</strong></h4><br>
a) Only dry type substation/transformers shall be installed.<br>
b) Entire installation of substation including switchgear room, capacitors, transformer etc. shall be
confirmed to the Indian Electric Act Rules in practice.<br>
c) Cables in the cable trenches shall be coated with fire retardant material.<br>
d) Automatic built-in circuit breakers shall be provided in the substation/transformer.<br>
e) The door of the sub-station shall be of two hours fire resistance.<br>
f) The capacity of the sub-station shall be as per service provider's requirement.<br>
g) All parts of switch gear and transformer are to be examined frequently and carefully for signs of
overheating, tracking etc.<br>
h) The substation/transformer area shall be kept prohibited and no unauthorized person shall be allowed
to enter in the area.<br>
i) Ventilation shall be provided at the ceiling level.<br>
J) H.V./L.V. cable ducts shall be as per Indian Electricity Rules.<br>
k) The danger signage on the substation with the electric voltage load.<br>
1) Two dry chemical power type (Class ABC type) fire extinguishers of 09 kgs. Capacity each with BIS<br>
certification mark coupled with four buckets filled with dry clean sand and shall be kept on the substation.<br>

<h4><strong>22. DISASTER MANAGEMENT PLAN:</strong></h4><br>
a) Disaster management plan for fire & other emergency shall be prepare and kept ready at the control
room.<br>
b) The mock drill with the designated fire marshal for any operation of disaster management plan shall
be
 carried out regularly after occupation as per National building code.<br>
c) Emergency exit route plan framed in glass shall be displayed in the common corridor, cross passages,
staircase lift lobbies of each floor level.<br>

<h4><strong>23. REFUGE AREA:</strong></h4><br>
<h3><strong>(A) Refuge area provided as shown in plan & shall be conforming to the following requirements:</strong></h3>
<p><strong>(i) Manner of refuge area</strong></p>
a) The refuge area shall be so located that it shall preferably face the wider open space on the side of the
building perpendicular to the main access road.<br>
b) The refuge area shall be provided with railing/ fire rated glass / parapet of 1.20mt.<br>
c) The refuge area shall have a door which 'shall be painted or fixed with a sign in luminous paint
mentioning "REFUGE AREA"<br>
d) The lift/s shall not be permitted to open into the refuge areas.<br>
e) The refuge area provided within building line shall be accessible from common passage/staircase.<br>
f) Access to Refuge Area shall be through a fire/smoke check door With minimum 2hrs fire resistance.
rating.<br>

<p><strong>ii) Use of refuge area :</strong></p>
a. The refuge area shall be earmarked exclusively for the use of occupants as temporary shelter and for
the use of Fire Brigade Department or any other organization dealing with fire or other emergencies
when occur in the building and also for exercises/drills if conducted by the Fire Brigade Department.<br>
b. The refuge areas shall not be allowed to be used for any other purpose and it shall be the responsibility
of the owner/occupier to maintain the same clean and free of encumbrances and encroachments at all
times.<br>
 c. Adequate emergency lighting facility shall be provided.<br>

<strong><p> Terrace floor as a refuge floor:</p></strong>
a. The necessary facilities such as emergency lighting, drinking water etc. shall be provided.<br>
b. The access door/s from the enclosed staircase/s to the terrace floor shall have louvers at top half portion
of the door.<br>
c. The entrance doors to the terrace shall be painted or fixed with sign painted in luminous paint mentioning
"REFUGE AREA".<br>

<strong><p>OBSERVATION & REMARKS</p></strong>
Adequate passageway and clearances required for the fire fighting appliances to enter the premises shall
be provided at the main entrance, the width of the entrance shall be not less than 6.00 meters. If an
arch or covered gate is constructed, it shall have a clear head-room of not less than 5 meters.<br>
 The other provisions of UDCPR & N.B.C. Part IV, 2016 should be strictly followed.<br>
 Before Issuing C.C., the Town Planning Department has to verify the Plan as per the given NOC
of Fire Department. & rectify the same. This is a Provisional No Objection Certificate, after providing the
above fire prevention and protection system and after compliance of above recommendations the Final No
Objection Certificate will be issued. Please note that this N.O.C.(Provisional) is not Development
Permission (C.C.) for commencement of work of building.<br>

<strong><p>The Party has paid the capitation fees of Rs. /- vide receipt No. dated
/ /2023 for the Total gross built up area ------------- Sq. mtr. as certified by the Architect vide his letter
Dated / /2023.</p><br>

<p>As per Maharashtra Fire Prevention and Life Safety Measures Act, 2006, Section 25-
Annexure-Part III, Fire Protection Fund Fees shall be levied and recovered by Fire Department and
Town Planning department is requested to verify the total built up area.</p><br>
<p>This is amended (Revised) Provisional NOC and these remarks are offered from fire risk
point of view only and necessary compliance of the Fire safety measures. Authenticity of the area,
premises, structure, trade activity, NA certificate of the land & earlier approvals etc, shall be verified
and confirmed by the concerned Town Planning Department and in case of any deviations this NOC
shall be treated as cancelled.</p></strong><br>

<p><strong>
    Note:<br>
1. The fire fighting installation shall be carried out by licensed approved agency.<br>
2. ADTP; Town Planning, MBMC is requested to scrutinized the plans as per amended DCR &
verify civil work and all other requirements pertaining to civil Engineering side including open
spaces, corridors, staircases, amendments, height, refuge area in sq. mtrs. & floor occupancy of
the building.<br>
3. This N.O.C. is issued from fire risk point of view only.<br>
4. Necessary permission for construction as well as any licensable activity shall be obtained from
concerned department of MBMC till then shall not be allowed to use.<br>
6. During construction stage and prior to final occupation party agreed to comply with additional
requirements, if any stipulated by this office and/or Fire Department Officer if any in future.<br>
7. There shall be no tree located in compulsory open spaces.<br>
8. The building is provided with all fire preventive measures with fireman lift. The fireman lift
as per NBC norms is provided with access to each floor by firemen during emergency.<br>
9. The NOC to occupation to the building under reference shall only be granted on inspection and
fulfillment of the compliance mentioned above by nominated/designated officer designated by
this office serving in Fire & Emergency Services, MBMC.<br>
10.Under Maharashtra Fire Prevention & Life Safety Measures Act, 2006 sub section (3) of section
3 it is the responsibility of the Owner/Occupier as the case maybe, shall furnish to The Chief
Fire Officer or Nominated Officer a Certificate in a prescribed form l.e. FORM "B" twice a
year in the month of January and July regarding maintenance of fire prevention and life
safety measures in good repair and efficient condition as specified in sub-sec (1).
</strong></p><br>

<p>The undersigned reserves right to amend any additional recommendations deemed fit during
the final inspection due to the statutory provisions amended from time to time and in the interest of the fire
safety of the buildings and in the interest of the protection of the people and same shall be complied with
before the Final Occupation.</p><br>

<p>Town planning department is requested to verify the total built up area and inform this office
and if same is found to be more for the purpose of levying additional capitation fees if required.
Thanking you, </p><br>

<div class="footer" style="float:right;">
        <p><strong>A. CHIEF FIRE OFFICER</strong><br>
        FIRE AND EMERGENCY SERVICES<br>
        MIRA BHAYANDAR MUNICIPAL<br>
        CORPORATION
    </p>
    </div>

    <br>
  <h3><strong>  COPY TO ARCHITECT WITH PLAN SUBMITTED WITH THE APPLICATION AT FIRE
DEPARTMENT.</strong></h3><br>
<p><strong>PLEASE NOTE:- The Fire Prevention & Life Safety Measures Act is Implemented in Mira- Bhayander
Municipal Corporation area from dated 01/01/2010, as per that The Fire Fighting Installation Work
should be done by Licensed Agency appointed by Maharashtra only. The list of the License Agencies is
available on www.maharashtrafireservices.org Or www.msfindia.org.</strong></p><br>

<strong>This N.O.C. is valid for 2 years from the date of issue.</strong><br>


</body>
</html>
